Shaktiran Delay of fan start after defrost Here you set the time that is to elapse from compressor start after a defrost and until the fan may start again. Enter contact details and we will notify you, when the product is available. Controller for temperature control — EKC Manual However the view of —d- will be discontinued if: Temperature signal 2 can be used for defrost stop based on temperature or for product sensor. Copying was not correct. Operating status The controller goes through some regulating situations where it is just waiting for the next point of the regulation.
|Published (Last):||6 February 2014|
|PDF File Size:||6.92 Mb|
|ePub File Size:||15.5 Mb|
|Price:||Free* [*Free Regsitration Required]|
Shaktiran Delay of fan start after defrost Here you set the time that is to elapse from compressor start after a defrost and until the fan may start again. Enter contact details and we will notify you, when the product is available. Controller for temperature control — EKC Manual However the view of —d- will be discontinued if: Temperature signal 2 can be used for defrost stop based on temperature or for product sensor.
Copying was not correct. Operating status The controller goes through some regulating situations where it is just waiting for the next point of the regulation. Ask for this product: When the time has expired the function will start a defrost. The extra temperature signal can be used for product sensor or for condenser sensor with alarm function.
The alarm will not become active until the set time delay has been passed. Low temperature alarm A4: If the settings in the controller are to be protected with an access code you can set a numerical value between 0 and An A alarm will not be visible as long as there is an active E alarm.
R22 Medium and high temperature scroll air-cooled condensing unit Open air outlet from side scroll ZB series.
There will be change-over to the normal time delay A03 when the temperature has dropped below the set upper alarm limit. A-alarms will not become visible until the set time delay has expired. Refrigeration stopped by thermostat S The temperature value is set. Refrigeration stopped because of open DI input S A special moulding technique unites the hard front plastic, the softer buttons and the seal, so that they become an integral part of the front panel.
The function is used as a simple defrost start, or it may be used as a safeguard if the normal signal fails to appear. Copying key not correctly mounted 5: Condenser temperature alarm E1: Refrigeration compressor or solenoid valve Defrost Alarm Refrigeration 2 compressor 2 Advantages: Ejc number or SW version do not match 9: When there is defrost with clock function on the DI input the interval time must be set for a somewhat longer period of time than the planned one, as the canfoss time will otherwise start a defrost which a little later will be followed by the planned one.
Relays The general connections are: ON-time in minutes Min. Defrost The controller contains a timer function that is zeroset after each defrost start. After two seconds you can move back into the mennu again and check whether the copying was satisfactory. We also inform you that: Icing-up will start a defrost. Hermetic Compressors c02 min. This page uses cookie files to provide its services in accordance to Cookies Usage Policy.
Faulmaran The relay cuts in eoc higher temperatures are required remember to cancel defrost functions and compressor functions. Basic temperature control, precise control Up to 3 relay outputs: Check delivery time and costs. Here are the messages that may appear: Sensor error on Sair E Push the upper or the lower button and select the new value 3. If this description is not sufficient, please send us a question to this product. The set value can be locked or limited to a range with the settings in r02 and r Relay output 2 can be used for alarm function or for cutin and cutout of a refrigeration step 2. Regulation is carried out when the input is short-circuited, and regulation is stopped when the input is put in pos. Thermostatic Expansion Valves flow direction: Sign me up to an availability notification.
Danfoss – Tækni framtíðarinnar nú þegar
Durisar But you can also use a sensor with another signal accuracy. Refrigeration stopped because of open DI input S Select your own number. If not, you can cancel the function with setting ekcc. This timer function can be used as a simple way of starting defrosts, but it will always act as safety defrost if one of damfoss subsequent defrost starts is not received. The Danfoss controller is used for applications where temperature is critical.
DANFOSS EKC 102D PDF
Kazrarn RA Box type air outlet from side Medium and high temperature scroll air-cooled condensing unit scroll ZB series. You can return the product without providing a reason within 14 days. Carton box Delivery Time: Notify me about a product availability. Temperature control, defrost control, fan control, panel embedded installation of small refrigeration equipment and cold storage d controller is simple to install, 16A high current relay output can not directly load intermediate relays, such as compressors, defrosting without parts, etc. Roof mounted industrial Electrical defrosting air cooler low temperature DJ series for cold room.
Danfoss 102 Installation & User's Instructions